Protective Coatings provides Secondary Containment solutions for:
• Oil and Gas Well Sites and Facilities
• Chemical Facilities and Storage Areas
• Tanks Farm Dikes or Berms
• Sumps and Trenches
• Drum Storage Areas
• Petroleum Storage
We offer a broad range of products and solutions to suit your needs:
• Polyurea (Pure & Hybrid) Plural-Component Coatings
• Multi-Step, Epoxy, Vinyl Ester & Urethane Systems
• HDPE Secondary Containment Solutions
• Koroseal® Membrane Systems
• Elastoline® Menbrane Systems
• Reinforced PVC Collector Pads
What are the secondary containment requirements?
Secondary containment systems must be:
- Designed, installed, and operated to prevent any migration of wastes or accumulated liquid out of the system to the soil, groundwater, or surface water at any time during the use of the tank system; and
- Capable of detecting and collecting releases and accumulated liquids until the collected material is removed.
To meet the requirements of paragraph (a) of this section, secondary containment systems must be, at a minimum:
- Constructed of or lined with materials that are compatible with the wastes(s) to be placed in the tank system and must have sufficient strength and thickness to prevent failure owing to pressure gradients (including static head and external hydrological forces), physical contact with the waste to which it is exposed, climatic conditions, and the stress of daily operation (including stresses from nearby vehicular traffic).
- Placed on a foundation or base capable of providing support to the secondary containment system, resistance to pressure gradients above and below the system, and capable of preventing failure due to settlement, compression, or uplift.
- Provided with a leak-detection system that is designed and operated so that it will detect the failure of either the primary or secondary containment structure or the presence of any release of hazardous waste or accumulated liquid in the secondary containment system within 24 hours.
- Sloped or otherwise designed or operated to drain and remove liquids resulting from leaks, spills, or precipitation. You must remove spilled or leaked waste and accumulated precipitation from the secondary containment system within 24 hours, or as promptly as possible, to prevent harm to human health and the environment.